|NEC Article 230 Page 4 of 6
230.70 Service Disconnect -
New text was added and it reads:
(A) Location of Service
(1) Readily Accessible. The service disconnect must
be located at a readily accessible location either outside the building or
structure, or nearest the point of entry of the service conductors.
Bathrooms. When the disconnecting means is installed indoors, it cannot be
installed in any bathroom.
Copyright © 2003 Mike Holt